beta_1                  Initial Ageing Rate
beta_2                  Forecast Ageing Rate
cof                     Consequences of Failure
cof_transformer_04_10kv
                        Consequences of Failure for a 0.4/10 kV
                        transformer
cof_transformer_11kv    Consequences of Failure for a 6.6/11 kV
                        transformer
current_health          Current Health score
dga_test_modifier       DGA Test Modifier
duty_factor_cables      Duty Factor for all cables (incl. submarine
                        cables).
duty_factor_transformer_11_20kv
                        Duty Factor for 6.6/11kV and 20kV Transformers
duty_factor_transformer_33_66kv
                        Duty Factor for 33/10kV and 66/10kV
                        Transformers and Tapchanger
e_cof_tf                Environmental Consequences of Failure for
                        transformers
environmental_cof_board_04kv
                        Environmental cost of Failure for 0.4kV Board
environmental_cof_cables_04_10kv
                        Environmental cost of Failure for 0.4kV and
                        10kV UG Cables
environmental_cof_cables_60_30kv
                        Environmental cost of Failure for 30-60 kV UG
                        cables
environmental_cof_ehv_cables
                        Environmental cost of Failure for EHV UG cables
                        & 132 kV UG cables
environmental_cof_ehv_fittings
                        Environmental cost of Failure for EHV/132kV
                        fittings
environmental_cof_ehv_switchgear
                        Environmental cost of Failure for EHV
                        swicthgear & 132kV CB
environmental_cof_hv_switchgear_distribution
                        Environmental cost of Failure for HV switchgear
                        distribution
environmental_cof_hv_switchgear_primary
                        Environmental cost of Failure for HV switchgear
                        primary
environmental_cof_lv_switchgear_and_other
                        Environmental cost of Failure for LV swicthgear
                        and others
environmental_cof_lv_ugb
                        Environmental cost of Failure for LV UGB
environmental_cof_ohl_cond
                        Environmental cost of Failure for Overhead line
                        conductors
environmental_cof_ohl_cond_50kv
                        Environmental cost of Failure for 50kV Overhead
                        Line Conductors
environmental_cof_ohl_fittings_50kv
                        Environmental cost of Failure for 50kV Fittings
environmental_cof_pillar_04kv
                        Environmental cost of Failure for 0.4kv Pillar
environmental_cof_poles
                        Environmental cost of Failure for Poles
environmental_cof_poles_ohl_support_50kv
                        Environmental cost of Failure for Poles OHL
                        Support 50kV
environmental_cof_relay
                        Environmental cost of Failure for Relays
environmental_cof_serviceline
                        Environmental cost of Failure for Service Lines
environmental_cof_sub_cables
                        Environmental cost of Failure for sub cables
environmental_cof_submarine_10kv
                        Environmental cost of Failure for 10kV
                        Submarine Cables
environmental_cof_submarine_30_60kv
                        Environmental cost of Failure for 30kV and 60kV
                        Submarine Cables
environmental_cof_switchgear_30_60kv
                        Environmental cost of Failure for 30kV and 60kV
                        Switchgear
environmental_cof_switchgear_primary_10kv
                        Environmental cost of Failure for 10kV
                        Switchgear Primary
environmental_cof_switchgear_secondary_10kv
                        Environmental cost of Failure for 10kV
                        Switchgear Secondary
environmental_cof_tower_ohl_support_50kv
                        Environmental cost of Failure for Tower OHL
                        Support 50 kV
environmental_cof_towers
                        Environmental cost of Failure for towers
environmental_cof_transformer_30_60kv
                        Environmental cost of Failure for 30/10kV and
                        60/10kV Transformers
environmental_cof_transformers
                        Environmental cost of Failure for Transformers
expected_life           Expected Life
f_cof_transformer_11kv
                        Financial Consequences of Failure for a 6.6/11
                        kV Transformer
ffa_test_modifier       Oil Test Modifier
financial_cof_board_04kv
                        Financial cost of Failure for 0.4kV Board
financial_cof_cables_04_10kv
                        Financial cost of Failure for 0.4kV and 10kV UG
                        Cables
financial_cof_cables_60_30kv
                        Financial cost of Failure for 30-60 kV UG
                        cables
financial_cof_ehv_cables
                        Financial cost of Failure for EHV UG cables &
                        132 kV UG cables
financial_cof_ehv_fittings
                        Financial cost of Failure for EHV/132kV
                        fittings
financial_cof_ehv_switchgear
                        Financial cost of Failure for EHV swicthgear &
                        132kV CB
financial_cof_hv_switchgear_distribution
                        Financial cost of Failure for HV swicthgear
                        distribution
financial_cof_hv_switchgear_primary
                        Financial cost of Failure for HV swicthgear
                        primary
financial_cof_lv_switchgear_and_other
                        Financial cost of Failure for LV swicthgear and
                        others
financial_cof_lv_ugb    Financial cost of Failure for LV UGB
financial_cof_ohl_cond
                        Financial cost of Failure for Overhead Line
                        Conductors
financial_cof_ohl_cond_50kv
                        Financial cost of Failure for 50kV Overhead
                        Line Conductors
financial_cof_ohl_fittings_50kv
                        Financial cost of Failure for 50kV Fittings
financial_cof_pillar_04kv
                        Financial cost of Failure for 0.4kV Pillar
financial_cof_poles     Financial cost of Failure for Poles
financial_cof_poles_ohl_support_50kv
                        Financial cost of Failure for Poles OHL Support
                        50kV
financial_cof_relay     Financial cost of Failure for Relays
financial_cof_serviceline
                        Financial cost of Failure for Service Lines
financial_cof_sub_cables
                        Financial cost of Failure for Sub cables
financial_cof_submarine_cables_10kv
                        Financial cost of Failure for 10kV Submarine
                        Cables
financial_cof_submarine_cables_30_60kv
                        Financial cost of Failure for 30kV and 60kV
                        Submarine Cables
financial_cof_switchgear_30_60kv
                        Financial cost of Failure for 30kV and 60kV
                        Switchgear
financial_cof_switchgear_primary_10kv
                        Financial cost of Failure for 10kV Swicthgear
                        Primary
financial_cof_switchgear_secondary_10kv
                        Financial cost of Failure for 10 kV Swicthgear
                        Secondary
financial_cof_tower_ohl_support_50kv
                        Financial cost of Failure for Tower OHL Support
                        50 kV
financial_cof_towers    Financial cost of Failure for Towers
financial_cof_transformer_30_60kv
                        Financial cost of Failure for 30/10 kV and
                        60/10 kV Transformers
financial_cof_transformers
                        Financial cost of Failure for Transformers
health_score_excl_ehv_132kv_tf
                        Health Score Factor for all Assets Categories
                        excl. EHV and 132kV Transformers
initial_health          Initial Health
location_factor         Location Factor (Excl.Submarine Cables)
location_factor_sub     Location Factor (Excl.Submarine Cables)
matrix_adjusted_circles
                        Adjust circles for matrix visualization
matrix_adjusted_intervals
                        Adjust banding for matrix visualization
mmi                     Maximum and Multiple Increment (MMI) Technique
n_cof_excl_ehv_132kv_tf
                        Network cost of Failure for all Assets
                        Categories excl. EHV and 132kV Transformers
network_cof_board_04kv
                        Network cost of Failure for 0.4kV Board
network_cof_cables_04_10kv
                        Network cost of Failure for 0.4kV and 10kV UG
                        Cables
network_cof_cables_60_30kv
                        Network cost of Failure for 30-60 kV UG cables
network_cof_ehv_cables
                        Network cost of Failure for EHV UG cabkes & 132
                        kV UG cables
network_cof_ehv_fittings
                        Network cost of Failure for EHV/132kV Fittings
network_cof_ehv_pole    Network cost of Failure for Poles
network_cof_ehv_sub_cable
                        Network cost of Failure for EHV /132 kV sub
                        cables
network_cof_ehv_switchgear
                        Network cost of Failure for EHV swicthgear &
                        132kV CB
network_cof_hv_lv_poles
                        Network cost of Failure for LV,HV,EHV Poles
network_cof_hv_sub_cables
                        Network cost of Failure for HV Sub cables
network_cof_hv_switchgear_distribution
                        Network cost of Failure for HV Switchgear
                        distribution
network_cof_hv_switchgear_primary
                        Network cost of Failure for HV Switchgear
                        Primary
network_cof_lv_switchgear_and_other
                        Network cost of Failure for LV swicthgear and
                        others
network_cof_lv_ugb      Network cost of Failure for LV UGB
network_cof_ohl_cond    Network cost of Failure for Overhead Line
                        Conductors
network_cof_ohl_cond_50kv
                        Network cost of Failure for 50kV Overhead Line
                        Conductors
network_cof_ohl_fittings_50kv
                        Network cost of Failure for 50kV Fittings
network_cof_pillar_04kv
                        Network cost of Failure for 0.4kV Pillar
network_cof_poles_ohl_support_50kv
                        Network cost of Failure for Poles OHL Support
                        50kV
network_cof_relay       Network cost of Failure for Relays
network_cof_serviceline
                        Network cost of Failure for Service Lines
network_cof_submarine_cables_10kv
                        Network cost of Failure for 10kV Submarine
                        Cables
network_cof_submarine_cables_30_60kv
                        Network cost of Failure for 30kV and 60kV
                        Submarine Cables
network_cof_switchgear_30_60kv
                        Network cost of Failure for 30kV and 60kV
                        Switchgear
network_cof_switchgear_primary_10kv
                        Network cost of Failure for 10kV Switchgear
                        Primary
network_cof_switchgear_secondary_10kv
                        Network cost of Failure for 10kV Switchgear
                        Secondary
network_cof_tower       Network cost of Failure for Towers
network_cof_tower_ohl_support_50kv
                        Network cost of Failure for Tower OHL Support
                        50 kV
network_cof_transformer_30_60kv
                        Network cost of Failure for 30/10kV and 60/10kV
                        Transformers
network_cof_transformers
                        Network cost of Failure for Transformers
oil_test_modifier       Oil Test Modifier
plot_pof                Plot of probability of failure
pof_132kv_cb            Current Probability of Failure for 132kV
                        Switchgear
pof_board_04kv          Current Probability of Failure for 0.4kV Board
pof_building            Current Probability of Failure for Primary
                        Substation Building and Secondary Substation
                        Building.
pof_cables_04kv_pex     Current Probability of Failure for 0.4kV UG PEX
                        Non Pressurised Cables
pof_cables_10kv_oil     Current Probability of Failure for 10kV UG Oil
                        Non Preesurised Cables (Armed Paper Lead)
pof_cables_10kv_pex     Current Probability of Failure for 10kV UG PEX
                        Non Pressurised Cables
pof_cables_132kv        Current Probability of Failure for 132kV cables
pof_cables_60_30kv      Current Probability of Failure for 30-60kV
                        cables
pof_cables_66_33kv      Current Probability of Failure for 33-66kV
                        cables
pof_ehv_fittings        Current Probability of Failure for EHV/132kV
                        Fittings
pof_ehv_switchgear      Current Probability of Failure for EHV
                        Switchgear
pof_future_board_04kv   Future Probability of Failure for 0.4kV Board
pof_future_building     Future Probability of Failure for Primary
                        Substation Building and Secondary Substation
                        Building.
pof_future_cables_04kv_pex
                        Future Probability of Failure for 0.4kV UG PEX
                        Non Pressurised Cables
pof_future_cables_10kv_oil
                        Future Probability of Failure for 10kV UG Oil
                        Non Preesurised Cables (Armed Paper Lead)
pof_future_cables_10kv_pex
                        Future Probability of Failure for 10kV UG PEX
                        Non Pressurised Cables
pof_future_cables_132kv
                        Future Probability of Failure for 132kV cables
pof_future_cables_60_30kv
                        Future Probability of Failure for 30-60kV
                        cables
pof_future_cables_66_33kv
                        Future Probability of Failure for 33-66kV
                        cables
pof_future_meter        Future Probability of Failure for Meters
pof_future_ohl_cond_132_66_33kv
                        Future Probability of Failure for 33-132kV OHL
                        Conductors
pof_future_ohl_cond_50kv
                        Future Probability of Failure for 50kV OHL
                        Conductors
pof_future_ohl_fittings_50kv
                        Future Probability of Failure for 50 kV
                        Fittings
pof_future_pillar_04kv
                        Future Probability of Failure for 0.4kV Pillar
pof_future_poles        Future Probability of Failure for Poles
pof_future_poles_ohl_support_50kv
                        Future Probability of Failure for Poles OHL
                        support 50 kV
pof_future_relay        Future Probability of Failure for Relay
pof_future_rtu          Future Probability of Failure for RTU
pof_future_serviceline
                        Future Probability of Failure for Service Line
pof_future_submarine_cables
                        Future Probability of Failure for Submarine
                        Cables
pof_future_submarine_cables_10kv_oil
                        Future Probability of Failure for 10kV Oil
                        Submarine Cables
pof_future_submarine_cables_10kv_pex
                        Future Probability of Failure for 10kV Non
                        Pressurised submarine cables
pof_future_submarine_cables_30_60kv_oil
                        Future Probability of Failure for 30kV and 60kV
                        Oil Submarine Cables
pof_future_submarine_cables_30_60kv_pex
                        Future Probability of Failure for 30kV and 60kV
                        Non Pressurised Submarine Cables
pof_future_switchgear_30_60kv
                        Future Probability of Failure for 30kV and 60kV
                        Switchgear
pof_future_switchgear_primary_10kv
                        Future Probability of Failure for 10kV
                        Switchgear Primary
pof_future_switchgear_secondary_10kv
                        Future Probability of Failure for 10kV
                        Switchgear Secondary
pof_future_transformer_04_10kv
                        Future Probability of Failure for 0.4/10kV
                        Transformers
pof_future_transformer_11_20kv
                        Future Probability of Failure for 6.6/11kV and
                        20kV Transformers
pof_future_transformer_132kv
                        Future Probability of Failure for 132kV
                        Transformers
pof_future_transformer_30_60kv
                        Future Probability of Failure for 30/10kV and
                        60/10kV Transformers
pof_future_transformer_33_66kv
                        Future Probability of Failure for 33/10kV and
                        66/10kV Transformers
pof_hv_switchgear_distribution
                        Current Probability of Failure for HV
                        Switchgear Distribution
pof_hv_switchgear_primary
                        Current Probability of Failure for HV
                        Switchgear Primary
pof_lv_switchgear_and_other
                        Current Probability of Failure for LV
                        switchgear and others
pof_lv_ugb              Current Probability of Failure for LV UGB
pof_meter               Current Probability of Failure for Meters
pof_ohl_cond_132_66_33kv
                        Current Probability of Failure for 33-132kV OHL
                        Conductors
pof_poles               Current Probability of Failure for Poles
pof_submarine_cables    Current Probability of Failure for Submarine
                        Cables
pof_switchgear_primary_10kv
                        Current Probability of Failure for 10 kV
                        Switchgear (GM) Primary
pof_switchgear_secondary_10kV
                        Current Probability of Failure for 10kV
                        Switchgear secondary
pof_tower_ohl_support_50kv
                        Current Probability of Failure for Towers OHL
                        support 50kV
pof_towers              Current Probability of Failure for Towers
pof_transformer_04_10kv
                        Current Probability of Failure for 0.4/10kV
                        Transformers
pof_transformer_11_20kv
                        Current Probability of Failure for 6.6/11kV and
                        20kV Transformers
pof_transformer_132kv   Current Probability of Failure for 132kv
                        Transformers
pof_transformer_30_60kv
                        Current Probability of Failure for 30/10kV and
                        60/10kV Transformers
pof_transformer_33_66kv
                        Current Probability of Failure for 33/10kV and
                        66/10kV Transformers
predict_weibull_model   Prediction function for Weibull model
present_value_future_risk
                        Present Value of Future Risk
risk_calculation        Calculates risk and converts to matrix
                        coordinates
risk_matrix_points_plot
                        Make a risk matrix with individual asset points
risk_matrix_structure   Makes a default risk matrix structure
risk_matrix_summary_plot
                        Make a risk matrix with non-linear spacing
s_cof_swg_tf_ohl        Safety Consequences of Failure for Switchgears,
                        Transformers & Overhead Lines
safety_cof_board_04kv   Safety cost of Failure for 0.4kV Board
safety_cof_cables_04_10kv
                        Safety cost of Failure for 0.4kV and 10kV UG
                        Cables
safety_cof_cables_60_30kv
                        Safety cost of Failure for 30-60 kV UG cables
safety_cof_ehv_cables   Safety cost of Failure for EHV UG cables & 132
                        kV UG cables
safety_cof_ehv_fittings
                        Safety cost of Failure for EHV/132kV Fittings
safety_cof_ehv_switchgear
                        Safety cost of Failure for EHV swicthgear &
                        132kV CB
safety_cof_hv_switchgear_distribution
                        Safety cost of Failure for HV Switchgear
                        Distribution
safety_cof_hv_switchgear_primary
                        Safety cost of Failure for HV Switchgear
                        Primary
safety_cof_lv_switchgear_and_other
                        Safety cost of Failure for LV swicthgear and
                        others
safety_cof_lv_ugb       Safety cost of Failure for LV UGB
safety_cof_ohl_cond     Safety cost of Failure for Overhead Line
                        Conductors
safety_cof_ohl_cond_50kv
                        Safety cost of Failure for 50kV Overhead Line
                        Conductors
safety_cof_ohl_fittings_50kv
                        Safety cost of Failure for 50kV Fittings
safety_cof_pillar_04kv
                        Safety cost of Failure for 0.4kV Pillar
safety_cof_poles        Safety cost of Failure for Pole
safety_cof_poles_ohl_support_50kv
                        Safety cost of Failure for Poles OHL Support
                        50kV
safety_cof_relay        Safety cost of Failure for Relays
safety_cof_serviceline
                        Safety cost of Failure for Service Lines
safety_cof_sub_cables   Safety cost of Failure for Sub cables
safety_cof_submarine_cables_10kv
                        Safety cost of Failure for 10kV Submarine
                        Cables
safety_cof_submarine_cables_30_60kv
                        Safety cost of Failure for 30kV and 60kV
                        Submarine Cables
safety_cof_switchgear_30_60kv
                        Safety cost of Failure for 30kV and 60kV
                        Switchgear
safety_cof_switchgear_primary_10kv
                        Safety cost of Failure for 10kV Switchgear
                        Primary
safety_cof_switchgear_secondary_10kv
                        Safety cost of Failure for 10 kV Switchgear
                        Secondary
safety_cof_tower_ohl_support_50kv
                        Safety cost of Failure for Tower OHL Support 50
                        kV
safety_cof_towers       Safety cost of Failure for tower
safety_cof_transformer_30_60kv
                        Safety cost of Failure for 30/10kv and 60/10kv
                        Transformer
safety_cof_transformers
                        Safety cost of Failure for Transformer
train_weibull_model     Training function for Weibull model
transformer_11kv_faults
                        Failure statistics dataset for 10,000 6.6/11kV
                        transformers
